Receive industry and products news from the market categories that matter to you most.
Stay up to date on industry news and trends, product announcements and the latest innovations.
HI Publishes Rotodynamic Pumps Guideline regarding NPSH Margin.
Press Release Summary:
Jan 24, 2013 - Hydraulic Institute (HI) has published ANSI/HI 9.6.1–2012 Rotodynamic Pumps Guideline for NPSH Margin, which serves asÂ replacement for 1998 edition. Covering rotodynamic, general-purpose pumps with power levels as high as 5,300 hp and impeller tip speeds less than 130 fps, guideline describes benefits to pump longevity of maintaining suitable NPSH Margin.Â Document serves as tutorial on NPSH while also providing guidance for determining NPSH Margin.
Original Press Release
Hydraulic Institute Publishes ANSI/HI 9.6.1-2012 Rotodynamic Pumps Guideline for NPSH Margin
Press release date: Jan 18, 2013
This guideline covers rotodynamic, general purpose pumps with power levels as high as 5300 hp and impeller tip speeds less than 130 feet per second and describes the benefits to pump longevity of maintaining suitable NPSH Margin. Pump users should be aware that “the full published pump head will not be achieved when the NPSH Available equals the NPSH3 of the pump. If the NPSH Available matches the NPSH3, the first-stage head will be 3% less than the fully developed value. Today’s higher speed, higher energy density pumps might not achieve acceptable service life under suction conditions without an adequate NPSH Margin.
This document serves as a tutorial on the subject of NPSH as well as providing guidance for determining NPSH Margin. The following considerations are discussed relative to the sensitivity of a pump to NPSH-related problems:
• Impeller inlet tip speed
• Larger vs. smaller impeller eye diameter
• Suction specific speed
• Characteristics of the pumpage
• Operating range of the pump and proximity to POR and AOR
• Materials of construction and cavitation resistance
• Impeller vane overlap
• Pump size and relationship of size to cavitation damage
• Duty cycle – time of operation under cavitating condition
• Reduction of NPSHA with time
This excellent NPSH reference helps pump users understand why it is essential to specify an appropriate NSPH Margin and learn about the negative aspects of specifying an excessive NPSH Margin.
The updated guideline is available for purchase at the HI eStore for $80.00 and is available in both hardcopy and pdf formats.
About the Hydraulic Institute: The mission of the Hydraulic Institute is to be a value-adding resource to member companies, engineering consulting firms, and pump users worldwide by developing and delivering comprehensive industry standards, expanding knowledge by providing education and tools for the effective application, testing, installation, operation, maintenance, and performance optimization of pumps and pumping systems, and by serving as a forum for the exchange of industry information. For more information on the Hydraulic Institute, its member companies and its Standards Partners, visitwww.Pumps.org. For information and registration details on educational offerings visit the Pump Systems Matter website atwww.PumpSystemsMatter.org.
Don't miss the latest news!